For more information and enrolment details please visit SolarQuip’s online registration website.
AS/NZS 5033:2014 has an exemption to the requirement to have a switch-disconnector between the PV array and the PCE (inverter, charge controller or load) for DC Conditioning Units.
… (c) Each input is limited to 350 W maximum PV power at STC and a maximum input voltage no greater than ELV.”
However, back in 2014 maximum module size was around 250W and this 350W limit seemed to allow any single module to be connected to a DCU such as those made by SolarEdge, Tigo etc… now, just three years later modules are heading over 300W and some nudging the 350W limit already.Interestingly, module manufacturers such as those listed below, already required covering of the module with an opaque material to limit any current before connecting or disconnecting the plug and sockets of a PV module. This manufacturer’s requirement provides a safe way to attach modules >350W @STC to a DCU and still ensure that the power in the cables is kept below 350W.
Covering with an opaque material also allows a safe (and no plug/socket damaging method) to disconnect a PV module from a faulty DCU (has gone short circuit internally).
I would argue that since the intent of the standard is to limit the power supplying the DCU to <350W, if following manufacturer’s installation instructions and covering the modules before disconnecting plugs and sockets, then modules larger than 350W@STC can be connected to a DCU and still meet the “no switch-disconnector on PV to PCE” exemption of clause 2.1.5.
List of module manufacturer’s who’s installation instructions require covering of the module with an opaque material:
- Ben Q
- Mitsubishi Electric
- Schuco mounting system
- SolTech Power
- First Solar
- SolarTech Micro Inverters
- International Energy Agency Photovoltaics in buildings
- AUO Photovoltaic Modules
- Sharp USA and UK
- Eging PV
- SunPower Modules & Inverters
- Suntech UL Install guide, Global install guide,
- Hareon Solar
- Grape Solar
- Perlight Solar
- Open Renewables
- ET Solar
- Fluitecnik Sun Energy
- Canadian Solar
- Shan Solar
- Cooper Crouse-Hinds Solar Recombiner, Array Fuse, Disconnect Box
- Mage Solar
- Solectria Renewables
- Solahart Australia
- Outback Power
- Advance Power
- SolarGain APS Micro Inverters
- Jinko Solar
- Moser Baer Solar
- Enhance Photovoltaics
- JA Solar
- Kyocera Solar
- DPSun Photovoltaic Modules
- Schutten Solar
- Soli Tek
- SunGrow inverters
- BOSCH solar modules
- Trina Solar
- Xantrex GT AU inverters
- Panasonic PV modules
- Samil Power Micro’s
- Phono Solar
- UPT Solar
- Shell Solar
*If you search the word “opaque” within these documents you will find the procedure to be universally applicable and acceptable.
Some of the exciting new systems at the Smart Energy Lab
Raj showing Mark how to commission the NicestESS 5kW AC coupled battery inverter. This unit can be used to add energy storage to any existing PV inverter system. The NicestESS unit is wired between the existing PV inverter and the switchboard to which it connects. The unit takes 48V Pylontech US2000B batteries.
Shaun and Steve discuss the Victron Energy system being installed into the new IP54 enclosure from Power Plus Solutions. The inverter is the new AS/NZS 4777.2:2015 compliant Multigrid 3kW hybrid inverter. The battery system is a GenZ pack of up to 6 x 3kWh units in the cabinet below.
Midwinter training courses at the Smart Energy Lab
Chula from Sungrow shows the students how to program the SH5K+ hybrid inverter.
New 5kW hybrid from Goodwe, the “EM” model. Same power rating (5kW) as it’s big brother (ES) but with a reduced 50A maximum battery charge/discharge current.
Upgrading an existing Outback system by adding another FM60, Hub and Mate3.
Configuring Suntrix’s myWatt inverter monitor.
Swapping over the GiantPower IPS4000 under harsh weather conditions.
Using the Solar Pathfinder to assess the solar window of a site.
Rachel doing a BMS hardware swap-over on the older Pylontech US2000A batteries.
Installing the new Imeon Energy 9.12kW hybrid inverter.
Duncan MacGregor from Enphase explaining how the Enphase system works.
Stage one of installing the EasyWarm “HotPV” system.
Networking at the end of the day on a cold winter’s night.
Mark configuring the EasyWarm system for both VOV and GT mode.
New products (above) for my students to install on the next course (30 May – 2 June). On every course, suppliers generously donate equipment for my students to train on. Next week we have: Goodwe EM hybrid inverter, NicestESS 5kW AC battery system, Gen2 Pylontech LFP 2.4kWh batteries, Victron 250/100 MPPT, EasyWarm HotPV system, Outback FM60 MPPT, myWatt energy monitor, Sungrow SH5K+ hybrid inverter and backup box plus lots more.
Our new Enphase training system
Enphase “Toolkit” App up on the big screen
Beau explains how he configured the Envoy-S
Beau checking the system performance
Brodie and Ralph working on the Goodwe BP and SolaX Hybrid system that they just installed.
Cameron explaining the configuration of the SolarEdge with Optimisers that they just installed.
Ben shows how to configure the SMA Sunny Island for off-grid installation.
Fotakis installing the Enphase Envoy-S in large switchboard.
John demonstrating the FIAMM molten salt battery
Bradley introducing the GenZ LiFePO4 battery.
Alan installing two Victron BMV700 battery monitors.
Mark showing students how to commission an Enphase system.
Aydin checking out the Envoy-S App.
Duncan & Mark showing how to mount Enphase micros on an indoor demo rail (panels are outside).
December 2016 Solar + Storage Course
The emphasis on our four day course is to blend theory and practice on a daily basis. The program starts with theory in the morning followed by practical sessions to reinforce and expand on the theory, returning to the classroom in the afternoon to explore the problems and solutions.
Many of the systems installed by students on this course are “real” systems. Above is a 1.5kWh/day system for the “Tiny House” located near the training centre. The house is a relocatable home for one person and has been designed from the ground up for minimal energy consumption. The solar panels the students installed were Solimpeks PVT (photovolatic and thermal) collectors. These unique panels combine water heating with electricity generation. Ideal for small roof areas such at this (7m x 2.5m).
“Beer o’clock” and system install review session! These “reviews” are part of the shared learning approach. Each team works on their own projects and come together at the end to present their experiences, likes and dislikes and problems.
Manfred explains how the Studer-Innotec d.c. coupled system works with Sonnenschein VRLA batteries.
Phil from Victron Energy shows the students how to program the 3kW Multiplus with 150/30 MPPT and ColorController.
“Capt. Col” working on the “Dream Team” – SP Pro + SolarEdge + LG Chem + Neuton Power VRLA. The concept of the “Dream Team” is to combine the high efficiency lithium battery with the low cost and depth of discharge capabilities of lead-acid batteries. The SolarEdge inverter meets the daily loads first from the LG Chem battery and only when depth of discharge limit is reached or the load power is greater than the power delivery limits of the lithium battery, is the lead-acid battery “called upon” via the Selectronic SP Pro to support the loads.
Ray carefully tensions battery terminals. Always use insulated tools when working on batteries with exposed terminals.
Ray & Adrian installing Studer XTM4000 and VarioTrack 150/80 MPPT. This d.c. coupled system gives high reliability and “battery centric” solar charging. D.C. coupling is a more reliable way of charging batteries and avoid the “black start” problem of a.c. coupled systems.
The “Tiny House” gets a power system.
David with GiantPower IPS4000 (dual MPPT/UPS inverter-charger)
Kevin, Col and Armin preparing the SolarEdge SE5000 with backup unit.
Ray connecting the Studer MPPT.
Jerry and Matt checking the Solar Analytics remote metering on GiantPower system.
Students install new Aquion BMS to integrate with Sunny Island 8.0H
The SMA Sunny Island inverter was primarily designed to work with lead-acid and (with the latest firmware) lithium ion battery systems. Integrating a non-lithium/non lead-acid battery with the Sunny Island has proved problematic, however, Aquion have solved the problem by building the DataTap device (BMS) that “emulates” the characteristic of a lithium battery BMS while managing the coulombic charging of the Aquion aqueous hybrid ion battery using it’s own current shunt.
Class photo with Aquion/SMA installation.
Ian Conibeer demonstrating the FIAMM molten salt battery
Jeff showing the Aquion BMS unit that he and Ben installed
Paul explaining the Schneider system installed with new Neuton Power VRLA tubular gel batteries